ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||27 May 2009|
|PDF File Size:||20.68 Mb|
|ePub File Size:||1.49 Mb|
|Price:||Free* [*Free Regsitration Required]|
The communicator is trouble free. Combination appliances individually inspected and tested. Modern smoke alarms will only switch low voltage i. Sensitivity tested results are recorded in the Device Test Record. For more information you can email us or telephone Please review additional Article 9 testing requirements on the Passive Systems page.
There are a total of: Will racks swing out of the cabinet at least ninety 90 degrees?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Batteries 2 charging current is normal Check pump coupling alignment? Description Type Model No.
Electrically Driven Pump Test Is the controller performing run tests automatically? Pipe and fittings shall be inspected from floor level? Visual indicator test lamp test operates. Quick opening devices passed test? A specific reference to the Standard on the front page of the report i.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Electrolyte level in batteries is normal Tighten electrical connection as required? Fire shutter release activated by fire alarm system? Each device tested while connected to control unit?
All sprinkler pressure regulating control valves passed full flow test? The fire alarm system documentation is on site and includes a description of the system. Direct Connection yes no Number of Conventional Zones: Fifth year inspection items.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Heat Tracing – check pipe insulation for cuts or abrasions. Combination multi-criteria detectors inspected and tested? Ylc leak at no flow? Valve supervisory switches indicate movement?
Yes No Time for motor to accelerate to full speed: Door glazing in good condition? Where possible, identify the date a fire detector is changed. Check heat trace controller interconnection to fire alarm system.
Reduced pressure assembly valves inspected for leaks or corrosion? When sufficient particles accumulate, the unit goes into an alarm condition.
Record anti-freeze Specific Gravity: Regardless of the type of detector your residence or building employs, there’s some additional maintenance you can perform to ensure the continued peak efficiency. C Tested and confirmed operation of alarm relay.